   ENG  Kurumsal     |       Ürünlerimiz       |        Referanslar  TrustAqua
Ana Sayfa Kurumsal Ürünlerimiz Teknik Makaleler Referanslar İnsan Kaynakları Hesaplama Araçları TDS and Electrical Conductivity Water hardness calculator Water analysis accuracy tester Osmotic pressure calculator Ion exchange calculator
İletişim  Ana Sayfa > Osmotic pressure calculator

# Osmotic pressure calculator

New Page 1
Osmotic pressure calculator
This calculator is under construction

This calculator determines the osmotic pressure of a solution containing dissolved solids. The osmotic pressure is based on theoretical calculations and gives you an indication about the operational pressure of a reverse osmosis system. The osmotic pressure can be calculated with the following formula: (1)

where: number of ions produced during dissociation of solute osmotic coefficient, unit less concentration of all solutes, moles/L universal gas constant, 0.083145 L·bar/moles·K absolute temperature, K

The factor i is also called the dissociation factor or the van't Hoff factor.

When you have a water analysis you often have the TDS in mg/L. The TDS does not give an indication about how the different solids are partitioned, it means that you cannot know the molar concentrations of the different solids dissolved in water. However, when you are making calculations for seawater the calculator spreads the TDS over Sodium (Na+) and Chloride (Cl-). This is possible because the concentration of these two elements is much higher than the concentrations for other elements in seawater.

The theoretical formula (1) used above is adapted to operational conditions by membrane manufacturers. Formula (2) is used by Dow / Filmtec to calculate the osmotic pressure: (2)

where: :sum of molality concentration of all constituents in a solution (moles of solute/kg of solvent)

The molality is calculated with the following formula: The obtained osmotic pressure with formula (2) is in psi (pounds per square inch). This calculator converts automatically the pressure to bar with the following conversion factor: 1 psi = 6.8948·10-2 bar.

If you do not have a water analysis you can use the values given in the right column in the input table. The values an indication about the standard seawater composition and brackish water. Click on the SW or BW button to put the values in the input fields of the table.

Table 1: Input table

 Element Concentration unit example Ammonium (NH4+) mg/L ppm g/m3 mol/L mmol/L 0.05 - Potassium (K+) mg/L ppm g/m3 mol/L mmol/L 3.3 390 Sodium (Na+) mg/L ppm g/m3 mol/L mmol/L 36 10900 Magnesium (Mg2+) mg/L ppm g/m3 mol/L mmol/L 6 1310 Calcium (Ca2+) mg/L ppm g/m3 mol/L mmol/L 84 410 Strontium (Sr2+) mg/L ppm g/m3 mol/L mmol/L 0.7 13 Barium (Ba2+) mg/L ppm g/m3 mol/L mmol/L 0.07 0.05 Carbonate (CO32-) mg/L ppm g/m3 mol/L mmol/L - - bicarbonate (HCO3-) mg/L ppm g/m3 mol/L mmol/L 265 152 Nitrate (NO3-) mg/L ppm g/m3 mol/L mmol/L 4.3 0.6 Chloride (Cl-) mg/L ppm g/m3 mol/L mmol/L 45 19700 Fluoride (F-) mg/L ppm g/m3 mol/L mmol/L 0.14 1.4 Sulfate (SO42-) mg/L ppm g/m3 mol/L mmol/L 24 2740 Silica (SiO2) mg/L ppm g/m3 mol/L mmol/L 9 5 Boron (B) mg/L ppm g/m3 mol/L mmol/L - 5 TDS mg/L ppm tds Temperature degree C degree F Kelvin

Table 2: Output table

 TDS mg/L ppm tds Total molality (mol/kg) Total molar mass (g/mol) Osmotic pressure (bar) Indication about operational pressure

If you want to eliminate one of the chemical elements given in table 1 Lenntech can look to your water analysis and propose you a reverse osmosis installation if it is suited for your application.
Please fill in the fields in the table Contact Information. You cannot send data if you don't give your name, country, Phone and Email.

Contact information

 Name * Company country * Email * Phone * Fax Comment

The indication about the operational pressure is given by multiplying the theoretical osmotic pressure by 2. As you can see in the formula the osmotic pressure depends on the temperature. So if you are in an environment with changing water temperatures calculate the osmotic pressure for different temperatures.

Warning: This calculator is accurate for the following parameters:

 20000 mg/L < TDS for SW < 43000 mg/L 100 mg/L < TDS for BW < 15000 mg/L 10° C < Temperature < 35° C

The calculations are made using 1 membrane with a production of 0,2 m3/h or (200 L/h).
The membrane used for seawater is the SW 30-4040 from Dow/Filmtec.
The membrane used for brackish water is the BW 30-4040 for Dow/Filmtec. İkitelli Organize Sanayi Bölgesi,Demirciler Sanayi Sitesi,
B2 Blok, No: 61, 34303, İkitelli / İSTANBUL

t : 444 1 239 (Türkiye'nin her yerinden alan kodu çevirmeden.)
f : 0212 671 10 70 Copyright © 2012 Ph Pompa Hidrofor ve Su Sistemleri San. Tic. A.Ş.